Voltage stabilizer SUNTEK 16000 VA Platinum is a popular model of the stabilizer, operating already at 100 volts of input voltage. Solves the difficult task - to work at full nominal even at very low voltage. SUNTEK Platinum relay stabilizers fully operate from 140 V input, but there are and there will be countries where there is not even 140 V in the electrical network, or the voltage periodically jumps. For these regions and were developed and launched a series of stabilizers Suntek series "Platinum".
To cope with the task of this series of stabilizers allow features, updates and additions that distinguish them from the classic relay stabilizers SUNTEK (Santek).
First of all, it is a more powerful coil (since the currents are higher compared to the network with voltage higher than 140V) installed in the stabilizer.
Secondly, it is the presence of 5 (five) relays to equalize the output voltage to the allowed level.
Thirdly, this forced cooling is implemented in two fans (coolers) that turn on when the winding reaches a temperature of 70 degrees Celsius.
Fourthly, the on-off stabilizer is carried out by a bipolar machine,
11000VA NN - 25 Amp automat (25x2 = 50A),
in 12500VA NN - 32A (32x2 = 64A),
16000VA NN - 40A (40x2 = 80A),
20000VA NN - 50A (50x2 = 100A). The bipolar automatic machine - additional reliability at transients in the automatic machine and at operation of the stabilizer.
Also, the SUNTEK stabilizer of the relay type 16000VA of the Platinum series, like all relay stabilizers, has a metal case (with holes for mounting on the wall and legs for horizontal installation), digital indication of the input and output voltage, on-delay (protection against false positives), short-circuit protection , overload protection, overheating protection, protection of the connected equipment against undervoltage, against overvoltage. Automatic shutdown and power up during a critical change in the supply network - if the input voltage suddenly exceeds 285V, the regulator will disconnect the load and will be in the standby mode of normalization of the network (below 285V), after which it will automatically turn on, and also at a critical voltage drop. The temperature mode of the stabilizer is from minus 30 to plus 50, the degree of protection of the enclosure is IP20.
3 year warranty
The SUNTEK 16000 Platinum voltage stabilizer will work even from 90 volts, but it should be understood that the load level must be less than the nominal. Its full-fledged characteristics of the stabilizer begins to perform from 100 volts. At a voltage in the range of 270-285 Volts, the actual output voltage will also be shown on the display. But when reaching 285-288 Volt, the stabilizer will immediately turn off by turning off all devices (the letter “H” on the display), since the output voltage will be very high and dangerous for the equipment.
The electronic unit of the SUNTEK Platinum relay voltage regulator is a powerful enough microcontroller, in which the input and output voltage is analyzed and the signals for key management are generated.stabilizer. When forming the control voltage, the microcontroller takes into account the response time of keys and power relays. This allows switching without breaks. As a result, the voltage waveform at the output of the relay stabilizer repeats the shape at the input.
The SUNTEK voltage regulator will be your network status indicator from 90 to 285 Volts. If you are interested, follow the state of the network, if you do not have time - the stabilizer will control everything himself and give the best option for this situation.
The voltage stabilizer has protection:
Short circuit protection
Overload protection (overheating)
Protection against impulse (lightning) discharges
Installation in a three-phase network for each phase will provide 52 kVA of power, and thereby eliminate the possibility of complete loss of the network. When connecting a three-phase load (machines, motors, etc.), it is enough to additionally install a phase control relay.
With this voltage stabilizer, we recommend installing our LOSS OF NEUTRAL PROTECTION SUNTEK development. This device protects your equipment from burning out if the voltage on the neural wire is lost. Overvoltage occurs mainly due to breakage of neutral conductors, when the supply voltage is distributed unevenly between consumers or due to errors of personnel serving the electrical network. An open conductor breaks or burns out when the electrical network is overloaded (the load on the network increases every year); under adverse weather conditions, when food is produced by an air line (wind, fallen tree); during short circuits in the electrical network; with poor contact at the junction of neutral conductors; when stealing non-ferrous metal (wire); with old wiring in the home network.
We recommend installing LOSS OF NEUTRAL PROTECTION SUNTEK in front of a voltage stabilizer, for example SUNTEK. At high voltages in excess of 285 volts, the voltage regulator disconnects the entire load from the power source, but remains itself at high voltage, waiting for a lower line voltage. To protect not only your house from burning, but also a voltage stabilizer, install such protection in front of a voltage stabilizer, and you will receive complete protection against any voltage fluctuations in the network. The stabilizer and LOSS OF NEUTRAL PROTECTION SUNTEK are synchronized at the same voltage, for example, for SUNTEK voltage regulators, this is 285 Volts, in this case it does not reduce the operating range of the stabilizer, LOSS OF NEUTRAL PROTECTION SUNTEK, but serves as its additional protection and protection against burning out the neutral conductor which has often become commonplace in cities and villages.